for Bellbrook, OH
here for a no cool call on a six year old Carrier air conditioner. Found failed capacitor on outdoor unit. Replaced capacitor and cycled system. Verified refrigerant charge is OK. System is running at a 7° Subcool and a 12 superheat. Customer said system froze up a couple weeks ago, but I cannot find anything that should have caused it to freeze up unless the filter was dirty. Charge is good, temp split is in range. Blower cap is within range. Blower and coil are Clean.
Arrived at customers house to install a Honeywell Prestige thermostat/EIM. The thermostat along with the interface module is wired correctly and set up for the customers application(heat pump w gas heat back up). System is running at a normal state at this time.