for Huber Heights, OH
Leslie - Huber Heights, OH
Chad was awesome! Explained the details of my heat pump and found a piece that was wearing out. Fixed in under an hour.
Chad was competent, courteous, explained everything
bob - Huber Heights, OH
Really good service and knowledgeable tech's..
Chris - Huber Heights, OH
Good service... and customer service
Customer stated unit is working again after changing filter. Wants to cancel call and will call back if it stops working again.
Turned unit on at stat system ignited ran for few mins then shut down with a pressure switch fault. On start up you could hear water inside of the inducer. Removed inducer and flue. Found a bug stuck in drain that connects flu pipe to collector box. Removed bug. Reinstalled inducer and flu. Restarted system. Ignited ran for few mins and shut down this time with high limit fault. Returning tomorrow to remove and clean blower as well as secondary heat exchanger
Customer advised that the previous day the heat had stopped working. Advised his roommate attempted to fix it and now they had no power to the nest thermostat Put the door back on the furnace. System powered up and began heating the house. As to the system blowing cool air the day before. Checked the flame sensor and had a reading of 0.06. Pulled and cleaned, sensor now testing 2.4
Customer stated that overnight her 2010 Goodman furnace had stopped. Heating. Further advised it would run for short time them shut off. Tested flame sensor which tested 0.03 Pulled and cleaned flame sensor and then restarted. Sensor now tests 2.6 Cycled system on and off several times with no issues each time running for longer than 3 mins. Ran system for 15 mins straight, system was on heating upon departure