for Jamestown, OH
found drain plugged. Blew out and flushed drain. Draining good now. Instructed customer on care and preventative maintenance.
1982 GE Furnace indoor blower is very dirty and blower capacitor is slightly week. 2005 Goodman Heat Pump outdoor unit also has a weak capacitor on the compressor side. Fan is also very noisy and drawing elevated amps. Spoke to him about some replacement options and he is not ready for an estimate at this time. Customer did not want to replace either weak capacitor at this time.
Found 2015 Trane Heat Pump unit to be overcharged. Adjusted charge down to a 12° sub cool. Even after doing this my superheat is still up over 20° and running around 22° even though it should be running around 14°. TXV at indoor coil does not seem to be functioning properly, and temperature split is poor. Will replace suction line and TXV for indoor coil.
Diagnostic Service Call on 2002 Ruud Air Conditioner. Service work performed: Here for a no cool on 18 yr old AC system. System has been freezing up recently. On arrival I checked filter and it is clean. Made sure both indoor blowers were coming on.(twinned furnaces) Checked refrigerant charge and found it slightly under charged. Running at a 40° superheat. Added 2 lbs. 2 oz. of R22 to achieve a 18° superheat. Advised customer there is likely a leak in the system. Just wanted to charge it up for now.