for Medway, OH
Diagnostic Service Call on Five Star AC unit, Service work performed: customer stated unit would not keep temp and was running all the time. Had customer replace dirty filter. Outdoor compressor sounded louder than should be making a hissing noise. unit was not level. Leveled unit using isolation pads Which quieted down the system. Further noticed unit was dirty and was cleaned with hose. checked pressures and 410a refrigerant was added to bring the system within manufactured recommended sub cooling levels.
Upon arrival, water started leaking from the coupling that connects the exhaust pvc and the elbow to the inducer motor. Removed the coupling and wiped it down and made sure they were not cracked. Re-inserted the coupling and fired up the furnace. Coupling may be bad. Informed customer that there could be water building up in the flue. Furnace is operational at this time.