Assisting customer with health issues attain heat.
Removed hose to open pressure switch on Ducane furnace. All is working properly at this time.
Replaced small section of wires and reconnected to board on Goodman furnace. The system is working well at this time.
Found dirty filter on Luxaire furnace. Replaced filter, and now the unit is running properly.
Diagnostic call placed.
Diagnostic service call
Goodman furnace repair