for Fairborn, OH
Kyle - Fairborn, OH
David - Fairborn, OH
Unbeatable service and pricing..!!
Jay - Fairborn, OH
Showed up right on time; quick, efficient, courteous, knowledgeable, just a great experience overall. 5-Star / Huber Heights H&C just became my only provider for all my HVAC needs.
here for a 18 year old air conditioner that is not cooling properly. Found system completely empty of refrigerant. Due to age and presence of a refrigerant leak, as well as cost of repairs would consider replacing. Property owner was not here on my visit and the person who met me here will relay this information to him and he will give us a call if he is interested in an estimate.
I here for a no cooling on a air conditioner we just installed two months ago. On arrival found breaker to outdoor unit was tripped only the indoor blower was running. Reset breaker and checked system amp draw. This is a 30 amp breaker and the system amp draw was only 7 A. This was likely a nuisance trip related to the storms last night. Advised customer if this happens again to call us back.
I here for a 10 year old air conditioner not cooling. On arrival found capacitor failed on outdoor unit. Replaced capacitor and cycled system. Verified refrigerant charge. System seemed to actually be a little bit overcharged, running at 2° superheat. Let out a little refrigerant to achieve a 8° superheat